The plate heat exchanger consists of a highly efficient heat transfer corrugated sheet and frame. The plate is clamped between the fixed pressing plate and the movable pressing plate by bolts, and a plurality of flow paths are formed inside the heat exchanger, and the plate is sealed with rubber. The crimping plate has a connector for connecting the device to the outside. The plate is pressed with a high-quality corrosion-resistant metal sheet, and the corners are filled with corner holes for the medium to enter and exit, and there are hanging holes on the upper and lower sides. Plate heat exchanger selection requires parameters
(1) The thermal power of a plate heat exchanger (for example, 1000 kW).
(2) The temperature of the inlet and outlet water on the primary side of the plate heat exchanger (for example: the inlet water temperature is 90°, and the outlet water temperature is 70°).
(3) The temperature of the inlet and outlet water on the secondary side of the plate heat exchanger (for example, the inlet water temperature is 60° and the outlet water temperature is 40°).